Back to eMart
|General Description:(GROUND FAULT CIRCUIT INTERRUPT)
GFCI Duplex Receptacle, 15Amp or 20Amp, 125V AC, 60Hz, 20A feed through.
Meets Latest UL Requirements .
Available Colors: white, ivory, almond, black, brown, gray and more.
|15 AMP||20 AMP|
GFCI: 15amp, buttons color match body face, no LED light.
GFCI: 15amp, buttons color match body face, with LED light.
GFCI: 20amp, buttons color match body face, no LED light.
GFCI: 20amp, buttons color match body face, with LED light.
2008 new features
If the GFCI consistently trips, it indicate end of life and GFCI must be replaced.
If GFCI end of life, redder the GFCI itself incapable deliver the power, denying
power to outlet & down stream.
Fast Block assures simultaneous power interruption at downstream receptacles and
Reverse Line-Load Measure Test- new design disables the RESET button function
(will not latch) when miswired. There will be no power to both outlet and downstream
In 2003 requirements, if GFCI line-load miswired, they only require no power to
"Line" side, but in 2008, require there is no power at both "Line" side and outlets.
2008 GFCI is required the end of life function
In the UL 943 requirements, when GFCI lose ground fault protection,
we called the GFCI end of life. When the GFCI end of life, it must be one of below:
A. use a visible or audible indication let the end users knows this
GFCI end of life and should be replaced.
B. Render the GFCI itself incapable deliver the power.
If within the two years from the date of purchase, this G.F.C.I. unit fails
due to defect in material or workmanship only, we will replace it free of charge.
The warranty does not apply to case of where damage has been due to faulty
installation, abuse, misuse, or unauthorized tampering and/or repair.